Before the installation of suspender, the installation position shall be determined first. After the determined installation position is accurately positioned with chalk and measuring tools, the drill shall be used to drill holes at the determined position and hit the expansion screw. The screw specification shall not be less than M8.
For the installation of dehumidifier, before the installation of dehumidifier, four sets of M8 nuts 1, elastic pad and flat pad shall be installed on the four expansion screws respectively, and then move the dehumidifier horizontally upward to thread the expansion screw into the lifting lug of dehumidifier, and then screw in a nut 2 respectively to install the dehumidifier on the expansion screw. It shall be noted that the dehumidifier shall not be inverted at any position, otherwise the dehumidifier will be damaged.
Horizontal installation, dehumidifier installed after adjusting the nut, can be detected with a horizontal ruler, so that the body to achieve horizontal installation, (so as to ensure that the dehumidifier can be normal water, to avoid water leakage), and finally nut installed dehumidifier locking, and then complete the installation of dehumidifier.
For the installation of drainage pipe, the dehumidifier shall be 5-250px higher than the drainage pipe. The length of drainage hose shall be determined according to the actual situation, but please ensure smooth drainage. The ceiling dehumidifier produced by the company can be either ceiling mounted or suspended. After installation, it shall be convenient for maintenance and air circulation.
For the installation of air inlet pipe, the air inlet shall be close to the machine body as far as possible, and the high-low level difference with the air inlet of the dehumidifier shall be as small as possible. The shorter the air inlet pipe, the better the dehumidification effect. The maximum length of the air inlet pipe shall not exceed 1.5m and shall be closely connected with the air inlet of the dehumidifier (there shall be no obstacles in front of the air inlet).
For the installation of air outlet pipe, the distance between the air outlet and the machine body shall be as far as possible, but the maximum length of the air outlet pipe shall not exceed 5m, the difference between the height and low position of the air outlet of the dehumidifier shall be as small as possible, and it shall be closely connected with the air outlet of the dehumidifier (there shall be no obstacles in front of the air outlet).